SZS series boiler is designed with longitudinal double drums and " D " type chamber structure. Furnace is placed on the right and convection tube bank is on the left, super heater is arranged at convection tube bank. The body is fixed on the basement by middle and both end flexible supports and make the boiler expand horizontally sideways. Around the furnace is membrane water cooling tube wall. Furnace and tube bank are totally separated by the membrane water tube cooling wall at the left side of the furnace. The back part of bundle is sparse shift structure, front part is aligned structure. Smoke from furnace outlet enters re-burning chamber, convection tube bank area and then from left front part enters spiral fine coil economizer and condenser, and finally is discharged to atmosphere through chimney.
Heat supplying, chemical, food, textile,
printing and dyeing, cigarettes and tobacco
(a) Big combustion chamber equipped with Low emission combustion burner effectively reduce the NOx to 30mg/m3. Smoke duct and smoke outlet use internal insulation to reduce operating noise.
(b) Combustion chamber uses full membrane water cooling wall structure and pressurized combustion without smoke mixture.
Good quality alumina silicate fiber and fire clay insulation material are used and the boiler body temperature is controlled below 45℃ and greatly heat loss is reduced. Combustion chamber is designed with narrow distance tube membrane water cooling wall which has good air proof to reduce heat lost and increase boiler thermal efficiency. Internal inspection holes uses high-alumina refractory and manhole cover seal devices, solving superheat problem in this part caused by using refractory bricks.
(a) Membrane structure are used in the front and back wall for boiler body and highly increased their lifespan to over 20 years.
(b) The key processes including material cutting, rolling, drilling are done by advanced CNC machining process to reduce the assembly stress and extend boiler service lifetime.
(c) Flutter prevention fastener is used for high temperature part convection tubes, which avoid convection tube cracking problem.
(d) Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will be tested by radiographic inspection.
SZS is equipped with two-stage steam separation device, which is conducive to the separation of steam and water gravity and improve the quality of steam; It can be saturated steam can also be superheated steam.